NOTICE TO WATER SYSTEM USERS
MAXIMUM CONTAMINANT LEVEL: NOTICE OF CORRECTION
The Long Beach Water System, I.D. 48000M, located in Pacific County.
What happened? What is being done?
The high TTHM results occurred in November 2019. To date, we have replaced filters at the water plant and researched water source treatments. In 2021 the city will expand the number of filters and treat the water source for organics. The city’s engineering firm is devising a plan that encompasses the progress that has been made thus far and other solutions that could be implemented. After the recent testing we are currently in compliance and are at a running average of 66.5 ug/L. The last six samples have read:
August 2019 = 110 ug/L, November 2019 = 130 ug/L, February 2020 = 96 ug/L, May 2020 = 45 ug/L, August 2020 = 50 ug/L and November 2020 =75 ug/L.
For more information, please contact Water Plant Operator Jake Binion at 360-642-3163 or P.O. Box 310, Long Beach, WA 98631, or David Glasson, Administrator, at 360-642-4421 or P.O. Box 310, Long Beach, WA 98631.
Please share this information with all the other people who drink this water, especially those who may not have received this notice directly (for example, people in apartments, nursing homes, schools, and businesses). You can do this by posting this notice in a public place or distributing copies by hand or mail.
This notice is being sent to you by City of Long Beach Water System on 12/16/2020.